Email has been sent to you , please check your spam/junk emails if you are unable to find the email.
Due to some internal error, the mail has not been sent.
Carrier's HVAC Controls 33ZCSENPAT primary air temperature sensor is required on a linkage coordinator zone controller if the zone controller is not using a CCN linkage compatible air source. The sensor is used to monitor the equipment's supply-air temperature. The temperature can be broadcast to the zone controllers which receive information from a linkage coordinator. The sensor has an operation range of -40 to 245 F.
The sensor consists of a thermistor encased within a stainless steel housing with 5 in. of exposed length. The sensor has 2 Teflon-insulated, stranded conductors.
Range of sensor is -40 to 185 F
Accuracy of ±0.36 F
Sensor encased within a stainless steel probe
California residents please see Proposition 65.